Knauf Insulation mineral fibre pipe sections HPS 035 AluR are wound and ground, non-flammable pipe sections made from Mineral Wool. The product has a jacket made from glass-fibre reinforced aluminium and is equipped with a self-adhesive closure in the longitudinal direction. Optimum insulating properties due to especially low thermal conductivity and high-precision shape as well as optimised concentricity are ensured by the modern production method with minimum production tolerances.
HPS 035 AluR Product Features:
- Length: 1200 mm
- Thermal conductivity (according to EnEV) of 0.035 W/mK at an average temperature of 40°C.
- Fire protection class A2 or A2L according to DIN EN 13501-1.
- Eurofins Gold Indoor Air Quality Standard.
- Very good thermal insulation.
- Easy to install
- Can be subjected to point loads and is inherently stable
- Tear-resistant tough surface.
- Attractive aluminium appearance.
- Resistant to ageing.
Made using ECOSE® Technology:
Knauf Insulation mineral wool products with ECOSE® Technology benefit from a formaldehyde-free binder made from rapidly renewable bio-based materials instead of petroleum-based chemicals which is up to 70% less energy intensive. The technology has been developed for Knauf Insulation’s mineral wool products, enhancing their environmental credentials without affecting the thermal, acoustic or fire performance. Insulation products made with ECOSE® Technology contain no dye or artificial colours – the colour is completely natural.
General mounting instructions:
To facilitate the opening the HPS 035 AluR pipe section for installation on the pipe work they are provided with a slight slitting on the side opposite to the longitudinal opening. This makes it much easier to push the shell over the pipe which is to be insulated. Before the longitudinal seam can be closed with the self-adhesive overlap, the protective strip must be removed. The strip can also be removed in sections. Ensure precise alignment of the halves of the pipe section before the self-adhesive coatings are pressed together. Firm pressure on the self-adhesive coating must be provided over the entire length of the longitudinal seam. The butt joints at the ends of the pipe sections must be sealed with self-adhesive aluminium tape.